Release Notes - Softwareupdate CMC III V 3.13.00

!!! Important information !!!

!- On Devices, which were delivered with software version V 3.11.00_1, the internal
sensors are set back to default once after the update. They have to be reconfigured
after the update has finished. Only LCP units are affected and only the internal
sensors of these are set back. Other sensor configurations and the general
configuration are not affected. Alternatively the configuration can be downloaded
via FTP before the update and uploaded again after the update to restore it.!

!- If a LCP is updated with the software version V 3.13.00, the LCP as device has to
be acknowledged again after the Update. This could be done by pressing the "C"-Button
in the front of the CMC III PU for 3 seconds or by clicking in the message list on
the website with the right mouse button and choosing the action "Acknowledge".!

!- The index of the both digital inputs at the backside of the CMC III Processing Unit
is swapped after an update from 3.09.00 (or lower) to a higher Software version and
matchs now with the labeling on the housing. If one or both of these digital inputs
is/are used as input of a Virtual Device or a Task, these Virtual Devices and/or Tasks
have to be adapted after the update.!

!- Because of new Variables and Configurations, the MIB of the CMC III has changed
and you must maybe adapt it again to a higher management system.
In general, the OIDs of the CMC IIII should be used with the ASCII-representation
instead of the numeral representation in a higher management system. If new variables
are added later, the numeral representation maybe does not fit any longer, but with
the ASCII-representation, still the right OIDs are addressed.!

!- If a normal CMC III PU from stock shall be used for a LCP or a RiMatrix S, a Patch-
file must be copied to this PU to declare it as LCP / RiMatrix S. If these file is
needed, please contact the service department from Rittal.!

- The CMC III Processing Unit will get new variables and the Sensor "CMC III PU" will
be pushed to the end of the sensorlist. To replace the "CMC III PU" back to the first
place in the list, the function "Reorganize" has to be choosen. Generally, Rittal
recommends to use the "Reorganize" function after the first installation of the system
and after every update, to keep the sensors every time in the same order.

- The power supply of the CMC III Processing Unit should not be removed while the
startup-process before the acoustic signal has sound or the website can be reached
again. Otherwise errors can occure.
- If a Virtual Device is defined, it can be changed automatically while the update
and show a "Changed" status after the update has finished. You only have to renew
the "Output" Variable of the Virtual Device. If you change the temperature unit and
a temperature value is declared as input of a Virtual Device, you also must choose
this value as input of the Virtual Device again.
- After the update of the CMC III PU all other sensors are updatet automatically.
The update-process is shown on the webpage and with a white blinkin at the LED in
the front of the CMC III Processing Unit.
- Please note the mentioned safety notes in the update manual.

Changes in V 3.13.00:
- Support of an SD card (not with CMC III Compact)
- Monitoring of the available memory and eject option of the SD card and USB stick
over the webinterface
- "CHarts": Logging of measured values on USB stick or SD card and display of graphs
on the webinterface (not with CMC III Compact)
- Firmwareupdate over Webinterface
- Additional languages can be choosen: German, Russian, Chinese, Spanish, French
- "Information"-field in the dialog "Access Configuration" added
- "Logging"-list can be printed as filtered list
- Support of the CAN-Bus DRC 7030.550 (RFID-system)
- New Device Rights-management for users
- New visualisation of Alarm- and Device Rights-Configuration of the sensors
- Graphical differentiation of the both data types "Config" and "Data"
- Expansion of groups to 32 groups
- Expansion of User to 33 User (32 individual User, 1 "admin")
- "Undock"-function to show the graphical sensorinformation in a own window of the
browser (function not supported by Internet Explorer)
- Expansion of possible logical combinations in the Tasks with operators "NOR" and
"NAND"
- New "Delay" function in the Tasks, whith "Switch Off Delay", "Switch On Delay"
and a pulsed switch is possible

Already known problems in V 3.11.40:
- With Internet Explorer 8, actions are executed very slowly. The Internet Explorer
9 or 10 should be used. Alternatively another Browser, f.e. Mozilla Firefox or Google
Chrome can be used.
- If one PSM busbar is connected to a CAN-Bus Unit and a second PSM busbar is added,
it can occure that both PSM busbars are lost in the system. In this case, the whole
CAN-Bus Unit has to be restarted by disconnecting it from the bus system. After the
restart, both PSM busbars are back again.
- In case 2 CAN-Bus DRC with RFID-Controllers are connected with a PU, it can happen
that a new Tag is not shown in the graphical view of the second controller. It is only
shown in the list-visualisation and also in the message-list in the lower area of the
website.
- Some Configurations are not shown right with the Internet Explorer. This problem
depends also on the Browser-Version. If the Website is not shown correctly by the
Internet Explorer, the browser has to be updated or alternatively another browser
has to be used.


Changes in V 3.11.00_5:
- Bugfix: Compatibility with Firefox 25 and Chrome 31
- Connection between FCS and CAN-Bus Unit improved

Changes in V 3.11.00_2:
- Added "Grouping"-function for CAN-Bus Sensor "CMCIII-SEN"
- Bugfix: Sender-Address is transmitted with a E-Mail

Changes in V 3.11.00_1:
- Bugfix: Security hole with wrong LDAP-request closed
- Bugfix: Faster access via FTP

New functions in V 3.11.00:
- Integration of IPv6 (not working with Server-Shutdown)
- DNS: In the general Configuration, servernames can be typed in instead of
IP-addresses (not working in the configuration of the Server-Shutdown)
- Integration of the communication protocol OPC-UA
- User management (only webside login) over LDAP
- Support of the new PSM measurement rails 7859.050 and 7859.053 with CAN-Bus
- Support of the new PSM-MID-Modules 7859.312 and 7859.332
- The unit of the temperature can be choosen between Celsius and Fahrenheit
- The system configurations can be downloaded in a configuration file from the
CMC III Processing Unit and restored again
- The name of the sensors and values are shown in the observation table
- Additional information over the webpage: status of the GSM-Unit, Power on the two
CAN-Bus Ports, System temperature, Power Supply
- The information about Serial Number is now shown in the observation in the
PU information
- Values of the Power Unit are shown in a graphical table
- The Universalsensor 7030.190 can be used as Wiegand-interface
- The Temperature-/Humiditysensor shows the Dew Point (calculated in the sensor)
- Right click in the tree structure or the message list shows different options for
easier management
- After clicking "Reorganize", sensors are acknowledged automatically. The defined
"Alarm Configuration" of the sensors are not set back to default
- Better Logging: More information are written in the Log-list with more information
- Better Overview in the Tasks: In the "Trigger Expression"-area, the actual
Expression is not shown any longer
- The Ethernet-Configuration can be choosen (only via Telnet or USB)
- Actions of sensors or modules can be done over Telnet
- General Software Maintenance
- The internal sensors of the CMC III Processing Unit are not "Lost" any longer
- Bug with the SMTP-communication with "Authentification" is fixed

New functions in V 3.09.00:
- Faster startup-process of the CMC III PU
- New design of the webinterface of the CMC III PU, analog to www.rittal.de
- New reboot function over the network via telnet
- Support of the Fan Control System 7320.810 with the CAN-Bus Unit for 2 channels
7030.030
- New Virtual Device "Access Controller" to switch outlets of CMC III sensors with
a CMC III reader system (Keypad and/or transponderreader)
- Graphical view of the PSM-Modules and tabular view of PSM busbars with
measurement
- Access codes and card codes can be programmed over the webpage
- New shutdown function for servers via RCCMD programmable over Tasks
- Higher number of input variables for Tasks
- PSM-Modules and other switchable outputs can be grouped and beacuse of this
switch together with only one definition. With PSM-Modules, max. 4 ports of one
module should be defined in the same group.